---
product_id: 632521695
title: "Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs)"
brand: "sqkmd"
price: "VT49475"
currency: VUV
in_stock: true
url: https://www.desertcart.vu/products/632521695-dixell-xr70cx-5n1c3-230v-50-60hz-digital-thermostat-controller-defrost
store_origin: VU
region: Vanuatu
---

# 230V/50-60Hz power compatibility Dual NTC probe inputs for precise temp control Integrated compressor & defrost alarms Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs)

**Brand:** sqkmd
**Price:** VT49475
**Availability:** ✅ In Stock

## Summary

> 🌡️ Stay cool, stay ahead — the thermostat pros trust!

## Quick Answers

- **What is this?** Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs) by sqkmd
- **How much does it cost?** VT49475 with free shipping
- **Is it available?** Yes, in stock and ready to ship
- **Where can I buy it?** [www.desertcart.vu](https://www.desertcart.vu/products/632521695-dixell-xr70cx-5n1c3-230v-50-60hz-digital-thermostat-controller-defrost)

## Best For

- sqkmd enthusiasts

## Why This Product

- Trusted sqkmd brand quality
- Free international shipping included
- Worldwide delivery with tracking
- 15-day hassle-free returns

## Key Features

- • **Robust Alarm System:** Instant alerts for compressor and defrost faults to prevent costly downtime
- • **Smart Fan Management:** Avoids short fan cycles and enables cyclical fan operation even when compressor is off
- • **Durable & Safe Design:** Engineered for medium-low temp units with moisture protection and secure probe placement
- • **Versatile Defrost Modes:** Choose between electric heater or hot gas defrost for tailored refrigeration cycles
- • **Precision Temperature Regulation:** Maintains optimal temps with dual probe inputs and positive differential control

## Overview

The Dixell XR70CX-5N1C3 is a high-precision digital thermostat controller designed for medium-low temperature ventilated refrigeration units. Featuring dual NTC probe inputs, versatile defrost modes, and smart fan control, it ensures efficient temperature regulation and system reliability. Its integrated alarms and robust design make it an essential tool for professional-grade refrigeration management.

## Description

Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs)

## Features

- The regulation is performed according to the temperature measured by the thermostat probe with a positive differential from the set point: if the temperature increases and reaches set point plus differential the compressor is started and then turned off when the temperature reaches the set point value again. In case of fault in the thermostat probe the start and stop of the compressor are timed through parameters “COn” and “COF“.
- Two defrost modes are available through the “tdF” parameter: defrost through electrical heater (tdF= EL) and hot gas defrost (tdF = in). Other parameters are used to control the interval between defrost cycles (IdF), its maximum length (MdF) and two defrost modes: timed or controlled by the evaporator’s probe (P2P).At the end of defrost dripping time is started, its length is set in the FSt parameter. With FSt =0 the dripping time is disabled.
- Forced activation of fans This function managed by the Fct parameter is designed to avoid short cycles of fans, that could happen when the controller is switched on or after a defrost, when the room air warms the evaporator. Functioning: if the difference of temperature between the evaporator and the room probes is more than the value of the Fct parameter, the fans are switched on. With Fct=0 the function is disabled.
- Cyclical activation of the fans with compressor off. When Fnc = c-n or c-Y (fans in parallel to the compressor), by means of the Fon and FoF parameters the fans can carry out on and off cycles even if the compressor is switched off. When the compressor is stopped the fans go on working for the Fon time. With Fon =0 the fans remain always off, when the compressor is off.
- Check the supply voltage is correct before connecting the instrument. Do not expose to water or moisture: use the controller only within the operating limits avoiding sudden temperature changes with high atmospheric humidity to prevent formation of condensation. Warning: disconnect all electrical connections before any kind of maintenance. Fit the probe where it is not accessible by the End User. The instrument must not be opened.

## Technical Specifications

| Specification | Value |
|---------------|-------|
| Manufacturer | SQKMD |
| Part number | Dixell-Jason202405290005 |
| Manufacturer reference | Dixell-Jason202405290005 |

## Images

![Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs) - Image 1](https://m.media-amazon.com/images/I/51ZMB5JKjdL.jpg)
![Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs) - Image 2](https://m.media-amazon.com/images/I/512ltDl1XJL.jpg)
![Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs) - Image 3](https://m.media-amazon.com/images/I/41Fiur8rSKL.jpg)
![Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs) - Image 4](https://m.media-amazon.com/images/I/41mBIhsSKpL.jpg)
![Dixell XR70CX-5N1C3 230V/50-60HZ Digital Thermostat Controller Defrost Fan Compressor Alarm for Medium Low Temperature Ventilated Refrigerating Units(with 2 NTC Probe Inputs) - Image 5](https://m.media-amazon.com/images/I/41qKsUPW8dL.jpg)

---

## Why Shop on Desertcart?

- 🛒 **Trusted by 1.3+ Million Shoppers** — Serving international shoppers since 2016
- 🌍 **Shop Globally** — Access 737+ million products across 21 categories
- 💰 **No Hidden Fees** — All customs, duties, and taxes included in the price
- 🔄 **15-Day Free Returns** — Hassle-free returns (30 days for PRO members)
- 🔒 **Secure Payments** — Trusted payment options with buyer protection
- ⭐ **TrustPilot Rated 4.5/5** — Based on 8,000+ happy customer reviews

**Shop now:** [https://www.desertcart.vu/products/632521695-dixell-xr70cx-5n1c3-230v-50-60hz-digital-thermostat-controller-defrost](https://www.desertcart.vu/products/632521695-dixell-xr70cx-5n1c3-230v-50-60hz-digital-thermostat-controller-defrost)

---

*Product available on Desertcart Vanuatu*
*Store origin: VU*
*Last updated: 2026-02-25*